Replaced a light fixture yesterday. For the hell of it decided to use my inductance tester at the bulb sockets. With the switch off, it still had current at the sockets.
This fixture is at the end of the line. It goes power cable to switch, then cable to light. Nothing after that.
Would this be an indication of a switched neutral or am I missing something? I looked in the switch box and it appears to be wired correctly. White wires tied together, black wires to the switch terminals......
Something screwed up "upstream" of the switch? Thanks.